Status: At its meeting on June 5, 2013, the Standards Committee rejected the revised SAR and approved curtailing the work on the original SAR.
Purpose/Industry Need: Repeated occurrences of generation shortfall in winter weather conditions in the southern United States, indicate that institutionalization of extreme weather preparation and reporting of generation availability is needed.
During the 2011 SW Cold Weather event, load shed was required to meet the demand due to loss of generation. During this weather event, cold weather conditions froze critical plant instrument sensors and equipment, causing generation to trip offline or not be able to come online to generate electricity when it was critically needed. Simultaneously, BAs and TOPs were basing their operations and operations planning on uncertain generation availabilities and capacities from the GO/GOPs, because the data available to them did not include availability based on severe winter weather. This uncertain information caused the BAs and TOPs to over-estimate the available generation, which resulted in the need to use load shedding to balance the actual available generation and load.
Based on the FERC-NERC report of the Southwest Cold Weather Event of February 1-5, 2011, in many cases, generation plants did not effectively utilize their cold weather maintenance practices that were in place to reliably perform under severe winter weather conditions. During the critical load time, many plants were in the mode of having to unfreeze equipment and make weather-proofing modifications in real time to keep plant equipment from freezing or refreezing. This subsequently caused generation to not be available during critical peak times, causing the GO/GOPs, BAs and TOPs to be unaware of the state of the generation resources. The FERC-NERC report concluded there would be a reliability benefit from amending the EOP Reliability Standards to require Generator Owner/Operators to develop, maintain, and implement plans to winterize plants and units prior to extreme cold weather, in order to maximize generator output and availability.
The SAR is being posted for a 30-day comment period through October 24, 2012 to gather additional input from the industry.
Draft SAR Version 1
Unofficial Comment Form (Word)
9/25/2012 - 10/24/2012
Standard Drafting Team Nominations
Info>> Submit Nomination>>
9/24/2012 - 10/8/2012
All comments should be forwarded to firstname.lastname@example.org.
home | account log-in/register | legal and privacy/trademark policy | site map | careers | contact us
Atlanta Office | 3353 Peachtree Road NE, Suite 600 North Tower, Atlanta, GA 30326 | 404-446-2560 Washington Office | 1325 G Street NW, Suite 600, Washington, DC 20005| 202-400-3000
Copyright 2021 North American Electric Reliability Corporation. All rights reserved.